Conductor : Circular compact stranded annealed copper
Conductor Screen : Semi conductive tape with extruded Semi-conductive cross-linked polyethylene (XLPE) compound
Insulation : Cross-linked polyethylene (XLPE) compound
Insulation Screen : Semi-conductive Cross-linked polyethylene compound
Water blocking tape : Semi-conductive water blocking tape
Metalic screen : Copper wires with copper contact tape
Water blocking and Cushioning tape : None-conductice water blocking tape
Radial water barrier : Copolymer aluminium tape
Sheath : Black polyethylene (PE), (Optional : with RIB)
Maximum conductor temperature : 90˚C
Maximum circuit voltage : 72.5 kV
AC test voltage : 90 kV
Preferably laid in subtations, factories and urban area. The cable shall be suitable for use in ducts, trays and direct burial in ground, subjected to immerse in water all time.
1768 Thaisummit Tower, 9th Floor, New Petchburi Rd., Bangkapi, Huai Khwang, Bangkok 10310, Thailand
88/8-9, 99/9 M.2 Ladbualuang-Maitra Rd., Ladbualuang, Ayutthaya 13230, Thailand.